 Research
 Open Access
 Published:
Engineering structural robustness in power grid networks susceptible to community desynchronization
Applied Network Science volume 4, Article number: 24 (2019)
Abstract
Networked power grid systems are susceptible to a phenomenon known as Coherent Swing Instability (CSI), in which a subset of machines in the grid lose synchrony with the rest of the network. We develop network level evaluation metrics to (i) identify community substructures in the power grid network, (ii) determine weak points in the network that are particularly sensitive to CSI, and (iii) produce an engineering approach for the addition of transmission lines to reduce the incidences of CSI in existing networks, or design new power grid networks that are robust to CSI by their network design. For simulations on a reduced model for the American Northeast power grid, where a block of buses representing the New England region exhibit a strong propensity for CSI, we show that modifying the network’s connectivity structure can markedly improve the grid’s resilience to CSI. Our analysis provides a versatile diagnostic tool for evaluating the efficacy of adding lines to a power grid which is known to be prone to CSI. This is a particularly relevant problem in largescale power systems, where improving stability and robustness to interruptions by increasing overall network connectivity is not feasible due to financial and infrastructural constraints.
Introduction
Disruptions of power grid systems can have a severe, negative impact on performance and lead to Coherent Swing Instability (CSI) (Susuki and Mezic 2011; Susuki et al. 2011; Susuki and Mezic 2012), whereby a subset of machines in the grid lose synchrony with the rest of the network, thus shutting the entire network down and leading to unacceptable blackouts. CSI is in essence a manifestation of community structure in a networked system, a collective dynamical divergence of one subgroup of nodal oscillations from another. Instigated by the work of Girvan and Newman on modular structures in networks (Girvan and Newman 2002; Newman and Girvan 2004; Newman 2006), a great deal of attention has been devoted to the development of methods for identification and characterization of modular components. Community detection has become a broadlydefined term which is used to refer to a variety of such approaches. A comprehensive review of its uses is presented by Schaub et. al. (Schaub et al. 2017). Much of the prominent work in the field has focused on topological approaches, i.e. methods which take as input an adjacency matrix describing a (weighted or unweighted, directed or undirected) graph. As Schaub notes, however, dynamics on a network are constrained by topology but cannot be fully described by it.
This distinction has led to work on community detection methods which place primary importance on dynamics. However, as many networks of interest lack a known set of laws governing their evolution (e.g. neurological, social, transportation, epidemiological, etc.), much of this research has modeled dynamics with Markovian diffusion processes describing random flows on the network (Delvenne et al. 2010; Rosvall et al. 2014; Bacik et al. 2016). Power grids have an advantage over these systems in that the physics of generator oscillations and current transmission are wellunderstood: taken in isolation, each node of the network behaves predictably. Only when they are combined on a complex and nonsymmetric graph structure do they begin to exhibit the group behaviors which resist simple characterization. In this work we seek to capitalize on this property by applying a dynamicsfocused community detection perspective to simulation data generated by a realistic, machinelevel power grid model.
Previous work on applying networktopological analysis to realworld power grids has met with mixed success. The extensive theoretical framework that has been developed in the field of Complex Networks has given rise to a variety of methods which assess functional properties of power grids directly from their network topology, using metrics such as node centrality, betweenness, degree distribution, community structure, and clustering coefficients (Cuadra et al. 2015; Albert et al. 2004; Bompard et al. 2015; Solé et al. 2008; Zhou et al. 2015; Xu et al. 2014; Pagani and Aiello 2014; Pahwa et al. 2013). However, topological methods alone have consistently failed to fully account for observed network vulnerabilities (Bompard et al. 2009; Bompard et al. 2010; Pagani and Aiello 2013; Hines et al. 2010). This has led to a variety of hybrid approaches which incorporate electrical properties of the system not captured by its graph structure, often by using them to assign edge weights or to compute modified versions of existing topological metrics (Nasiruzzaman et al. 2011; Hines et al. 2010; Yan et al. 2013; Bompard et al. 2010; Bompard et al. 2012). The goal of these studies has generally been to develop a heuristic to estimate a power grid’s vulnerability to failure, which they then validate using historical data or numerical simulations. In this work we present an alternative method which evaluates the functional consequences of structural modifications directly from simulation data. While this approach has previously been applied to steadystate systems (Baldick et al. 2009), its use for grid disturbances has generally been dismissed as infeasible due to the combinatorially large search space of possible faults and network structures (Hines et al. 2010). Our contribution is a methodology for incorporating topological properties (specifically, community structure) and statistics on measurement data to significantly reduce this space. Our technique identifies a set of candidate locations for singleline additions to an existing network; this is a small structural perturbation relative to the size of the full grid and therefore unlikely to significantly change its global topological characteristics, such as degree distribution. Robustification occurs not by directly tuning some topological (or hybrid topological/electrical) metric, but rather by using such a metric to inform a minor structural modification. This lends itself to practical engineering application, as it suggests an inexpensive change that could be made to an existing grid rather than a design principle for the construction of a new grid from the ground up.
Our datadriven approach is motivated by the proliferation of realtime monitoring strategies for power grids that have been deployed in recent years (Messina and Messina 2015; Kezunovic et al. 2013; Barocio et al. 2013), with event location strategies gaining increasing attention in order to localize pernicious effects (Li et al. 2010; Mei et al. 2008; Bhui and Senroy 2016). These strategies are directed to provide a systemwide awareness of events such as faults and other disturbances, taking advantage of the increasing coverage of wide area measurement systems (WAMS) technology which enables the implementation of wide area emergency and restorative control applications (Li et al. 2010; Mei et al. 2008; Bhui and Senroy 2016). Even though these strategies have achieved positive results, additional technical challenges arise as the modern WAMSgenerated data become high dimensional and more distributed thorough large areas of the system. We propose an additional technique for power grid network robustification. Specifically, we show that the robustness of the network can be diagnosed from ensemble fault simulations. Moreover, the power grid can be made significantly more robust to disturbances with proper engineering of the network design and attention to the community structure observed in instances of CSI. Such considerations are critical in considering future power systems deployments, or for upgrading current networks in order to circumvent susceptibility to CSI.
In this paper, we detail a simulation model used for characterizing the power grid dynamics and disruptions. We further introduce a procedure for dynamicsbased community detection based on the results of these simulations, showing through diagnostic tools that the network’s sensitivity to CSI depends on the location and severity of a fault. This allows us to provide an engineering approach capable of characterizing network connectivity modifications capable of robustifying the network to decoherence.
Numerical Simulations of Power Grids
In this section, we highlight the numerical simulation architecture used to evaluate power grid systems and their connectivity structure. Importantly, a prescription of the disturbances applied to the network to induce CSI is considered in order to evaluate the network robustness in a principled way.
The Power System Toolbox
Power grid simulations for this study were produced using Power System Toolbox (PST), a Matlab software package originally developed by Kwok W. Cheung and Joe Chow of Rensselaer Polytechnic Institute (Chow and Cheung 1992). Supplied with both the topological structure of a power network and the specific electromechanical parameters of the grid’s generators, nodes, and lines, PST performs dynamic simulations of both steadystate and nonequilibrium dynamics. In this study we employ system fault simulations structured as follows:

1.
The system is initialized in a steady state for power flow through the network by solving the nonlinear algebraic network equations which specify the load flow problem.

2.
The dynamic portion of the simulation is initiated by applying a transient threephase fault to a single line in the network, as though the line were brought into momentary contact with a grounding object such as a tree.

3.
When a fault occurs, power system protection equipment acts to isolate the disturbance. If the fault is transient, the line can be reconnected after a short time. PST treats this as a twostep process, clearing the fault first at the near end and then at the remote end of the line. These two time intervals, labeled in this paper as τ_{1} and τ_{2}, are supplied as input parameters in simulations. Figure 1 illustrates the two time scales, τ_{1} and τ_{2}, for a simulation of the northeastern power grid system. Our interest is in the dynamics following the fault application and fault clearing time scales.

4.
When the fault is cleared, the grid recovers its full original network structure. The fault has perturbed it from its initial steadystate configuration, so dynamic evolution continues. We continue the simulation for a long time (relative to the fault duration) and analyze the network’s response to the disturbance. The CSI often is induced by a disturbance event (fault application) for which the power grid system does not recover to its original stable (steadystate) behavior.
The NPCC 140Bus System
Simulations in this study are carried out on the NPCC 140bus test system, which is a reduced model based on the power grid of the North American northeast (Fig. 2). This network was chosen because its machine parameters are representative of those in a major realworld grid and its graph structure is sufficiently large and complex that it gives rise to coherent dynamics at subnetwork level.
Discovering Community Structure in the Grid
Simulations of the northeastern power grid are sufficient to illustrate many of the key features of power grid networks and their induced CSI. By perturbing the various nodes of this specific network, we can characterize the instability structures, and their commonalities, induced in the power grid dynamics.
Identifying Coherent Swing Instabilities
The focus of this specific study is the phenomenon of CSI, in which a subgroup of buses which are strongly coupled to one another, but only weakly coupled to other nodes, collectively lose synchronicity with the remainder of the network. Realworld power systems implement controllers to damp the oscillations of relative rotor angles which give rise to CSI, but no such safeguards are implemented in the PST simulation toolbox. The onset of CSI therefore is manifested as a clear qualitative transition in the dynamics of a subset of the buses. Specifically, a group of machines will begin to oscillate with linearly increasing frequency while the remainder of the network continues to evolve with dynamics on a slower and roughly constant time scale (Fig. 3). Although the PST model does not accurately model the behavior of the unstable network, since local controllers would activate to dampen growing oscillations, it does highlight the lack of robustness of the network to the intrinsic dynamics induced by the disturbances. By engineering a more robust system, the intrinsic dynamics itself acts to stabilize the system. This aspect of engineering a power grid network is considered below in the section entitled Engineering Network Structure to Reduce CSI.
Community Detection
We begin by investigating the incidence of CSI by systematically applying faults to each line of the network in succession and tracking which buses (if any) exhibit unstable dynamics as a result. The results, plotted in Fig. 4, suggest that the majority of instabilities take place in a particular subgroup of buses. To formally characterize this structure we approach it as a network community detection problem: by treating the buses and fault locations as two disjoint populations of nodes with (unweighted, undirected) connections given by the nonzero elements in Fig. 4, we build a square adjacency matrix which casts the results as a bipartite instability matrix (with (N_{bus}+N_{line}) rows and columns).
In this form, the results are amenable to any networktopological community detection scheme desired. Results presented in this paper use the Adaptive BRIM algorithm, developed by Michael J. Barber for modularitybased community detection in bipartite networks (Barber 2007). Very similar results were obtained using other bipartite algorithms, including those introduced in Newman (2008) (Newman 2006) and Liu and Murata (2009) (Liu and Murata 2009).
The Adaptive BRIM algorithm detected 12 distinct communities from the bipartite instability matrix. However, many of these were quite small. In the interest of restricting focus to networkwide swing instabilities, communities containing fewer than 2 buses or lines were reassigned to a neighboring cluster based on a vote of graphical nearest neighbors. This led to a reduced population of 3 dominant communities, plotted in Fig. 5.
The blue community, which corresponds geographically to New England, is a contiguous and highly interconnected nodal group with few connections to the rest of the network. A simple topological community detection scheme applied directly to the NPCC140 graph would almost certainly have identified it as a highly modular cluster. The purple group, however, is thoroughly embedded within the larger black nodal population. This is a testament to the importance of our dynamicsbased approach to community identification: modular graphical structure does not necessarily equate to dynamical coherency.
The Sensitivity of Network Connections
Given the diversity of dynamics observed for disruptions of the network, our analysis aims to understand the sensitivity of each node in the power grid to fault tolerances. By varying the fault severity, we can rank the nodes and their susceptibility to CSI.
Varying Fault Severity
To identify the lines where a system fault is most likely to generate CSI, we measure responses to faults of varying intensity. Faults in PST simulations are parameterized by two time durations: τ_{1} from the application of the fault to the clearing of the near end, and τ_{2} from the clearing of the near end to that of the remote end. Generally speaking, a longer fault duration drives the system farther from its initial steadystate configuration, increasing the likelihood of instability. Indeed, the parametrization of faulty intensity through the (τ_{1},τ_{2}) parameter space allows us to characterize the robustness of each node.
Ranking Lines by Sensitivity
Working in (τ_{1},τ_{2}) parameter space, we identify a domain which captures the onset of instability for most fault locations. This gives a range of values broad enough so that the lowest values of τ_{1}, τ_{2} yield fully stable dynamics, while the highest values of τ_{1}, τ_{2} lead to instability at many fault locations. The precise choice of bounds is somewhat arbitrary as long as they meet these criteria; the performance over the specified (τ_{1},τ_{2}) region will only ever be used as a relative metric for comparing lines. For each fault location, we repeat simulations over a grid in this domain of parameter space. The performance of each run is quantified by determining the number of buses which go unstable.
The result of this analysis gives an “instability frontier” in the space of (τ_{1},τ_{2}). As visualized in Fig. 6, the more sensitive lines of the network (e.g. Fig. 6a) have a frontier which extends farther down toward the bottomleft corner, whereas more robust lines (e.g. Fig. 6b) are fully stable until comparatively high values of (τ_{1},τ_{2}). In the former case, we observe that a small perturbation to the fault parameters can lead to a big jump in the number of unstable generators. This foreshadows the crucial role of community structure in understanding this behavior: instability often occurs collectively in coherent subnetworks.
Having performed exhaustive simulations for all possible fault locations, we rank lines according to sensitivity by averaging over the unstable nodes obtained at all (τ_{1},τ_{2}) parameter combinations. The numerical values obtained are of course sensitive to our choice of the faulttime domain, but they serve as a functional metric of comparison between different lines tested on this domain. Figure 7 illustrates the results of this process, with the 20 most sensitive lines highlighted in red. These are the lines whose performance we seek to improve through the remainder of this study. The network modifications we consider in the next section belong to a combinatorially large space, so it is necessary to restrict the scope of our analysis wherever possible to avoid having to do a prohibitively large number of simulations. Restricting simulations to these “worst offender” fault locations allows us to constrain the parameter space while still treating the cases which are of greatest practical concern with respect to grid stability.
Engineering Network Structure to Reduce CSI
Although the specific criteria which lead a subgroup of buses to coherently desynchronize in a given network are not generally well understood, it is clear that the observed phenomenon of community structure is intimately related to the connectivity configuration of the network. Grids are prone to CSI when they contain a subnetwork which is relatively weakly coupled to its surrounding nodes. Thus a naive approach to engineering network stability would be to simply add connections between nodes inside and outside this instability prone community. The results we present in this section not only support this intuition, but also show that not all intercommunity line additions yield significant improvements to stability. As such, the full simulationbased approach implemented here is necessary to determine which intercommunity connections contribute the most to the grid’s structural robustness.
Network Modification Protocol
The approach for assessing how the addition of a transmission line affects the incidence of CSI is as follows:

1.
A line connecting the two chosen buses (with resistance and reactance specifications taken to be the median of those of the existing lines) is inserted into the PST network specifications.

2.
For each of the most sensitive lines in the unmodified network (i.e. those highlighted in Fig. 7), simulations are carried out for all (τ_{1},τ_{2}) faulttime combinations in the domain identified previously to obtain an instability frontier (denoted in Fig. 8 by a black dotted line).

3.
Overall performance for each fault location is again obtained by averaging over the sum of unstable generators. These values are then averaged over all tested fault locations to obtain a single plot of the modified network’s susceptibility to CSI (shown in the right column of Fig. 8).

4.
The result of this process is compared to that of the unmodified network to obtain a ratio measuring the stability improvement afforded by the added connection.
The set of possible singleline additions to the network is combinatorially large (N_{additions}=N_{bus}(N_{bus}−1)−N_{line}=19367, in the case of the NPCC140 system). The number of simulations necessary to carry out the above steps for a single network modification is such that it is not computationally feasible to test all possible cases.
We present results on a semirandomly selected subset of these possibilities (“semirandom” because they were chosen with a penalty on geographic distance between the buses to be connected, so as to better conform to practical engineering considerations). These candidates are separated into two groups: those which run between two distinct communities, and those which are internal to a single community.
Network Modification Results
The candidate lines tested using the above protocol are pictured in Fig. 9, colored according to their performance relative to the original network configuration. Additionally, the distributions of the stability change parameter for each of the two populations of line candidates are presented as histograms and box plots in Fig. 10.
We observe that every line addition that significantly impacted the network’s susceptibility to CSI is one that connects two distinct communities. This suggests that understanding the network’s community structure is crucial to identifying candidates for new lines to robustify the grid. The search space of intercommunity lines is substantially smaller (\(N_{\text {additions}} = \frac {1}{2}\sum _{i}^{N_{\text {community}}} \left [N_{\text {bus}}^{i} \left (N_{\text {bus}}^{\text {tot}}  N_{\text {bus}}^{i} \right)\right ]  N_{\text {line}}^{\text {inter}} = 4191\), in the case of the NPCC140 system, which represents a 79% reduction of the search space). Coupled with practical distance considerations (and any other logistical criteria such as local topography or infrastructure), the number of line candidates for which this extensive simulation process must be carried out becomes much more tractable.
Within the intercommunity population of line candidates, the criteria for significant robustification are not obvious. Examining the relationship between performance and common topological metrics such as betweenness and degree centrality reveals little to no correlation, which supports the literature consensus (Bompard et al. 2009; Bompard et al. 2010; Pagani and Aiello 2013; Hines et al. 2010) that these measures are insufficient as predictors of behavior in real power systems. Nonetheless, we have successfully identified a number of lines which do offer a marked improvement even by testing a very small subset of all possible intercommunity connections. This shows that our approach to evaluating robustness of the network can effectively identify potential connections capable of robustifying the power grid network.
Conclusion
We propose a computational framework for the analysis of the network level dynamics and stability of power system disturbances. Our analysis is critical for understanding how the network architecture itself can lead to subgraphs (communities) that are highly susceptible to CSI. By systematically parametrizing disturbances according to the temporal parameters τ_{1} (the time of the fault until it is cleared) and τ_{2} (from the clearing time of the near end to that of the remote end), we can assess the effect of each node on the overall stability of the power grid network.
We specifically develop evaluation metrics to (i) identify dynamicsbased community substructures in the power grid network, (ii) determine weak points in the network that are particularly sensitive to faults, and (iii) produce an engineering approach for the addition of transmission lines to maximally reduce the incidence of CSI. For our example of the Northeast power grid, we identify a strong dependence of line sensitivity on the New England subnetwork. We show how modifying the network’s connectivity structure can robustify the network to CSI. The space of possible connectivity changes is combinatorially large, so we restrict modifications to a tractably small subset of singleline insertions to the original network. We show that community detection can be used to substantially reduce this search space, as line additions which connect separate communities tend to much more significantly impact global stability. We find that the addition of a line can markedly improve the grid’s resilience to CSI, but the success is highly dependent on location within the network.
Our analysis provides a versatile diagnostic for the efficacy of adding a particular line to a power grid which is known to be prone to CSI. This is a particularly relevant problem in largescale power systems, where improving stability by increasing overall network connectivity is not feasible due to financial and infrastructural constraints. Our approach focuses principally on network topology, so its results are fairly robust to small variations in the model parameters used in simulation. This makes it a strong candidate for use in analyzing realworld power systems, as connectivity structure is a characteristic which can be perfectly reproduced in the translation from physical system to simulation model.
References
Albert, R, Albert I, Nakarado GL (2004) Structural vulnerability of the North American power grid. Phys Rev E  Stat, Nonlinear, Soft Matter Phys 69(2 2):1–10. https://doi.org/10.1103/PhysRevE.69.025103. 04010840401084.
Bacik, KA, Schaub MT, BeguerisseDíaz M, Billeh YN, Barahona M (2016) Flowbased network analysis of the caenorhabditis elegans connectome. PLOS Comput Biol 12(8):1–27. https://doi.org/10.1371/journal.pcbi.1005055.
Barber, MJ (2007) Modularity and community detection in bipartite networks. Phys Rev E 76:066102. https://doi.org/10.1103/PhysRevE.76.066102.
Barocio, E, Pal BC, Fabozzi D, Thornhill NF (2013) Detection and visualization of power system disturbances using principal component analysis In: Bulk Power System Dynamics and ControlIX Optimization, Security and Control of the Emerging Power Grid (IREP), 2013 IREP Symposium, 1–10.. IEEE.
Bhui, P, Senroy N (2016) Application of recurrence quantification analysis to power system dynamic studies. IEEE Trans Power Syst 31(1):581–591.
Bompard, E, Napoli R, Xue F (2009) Analysis of structural vulnerabilities in power transmission grids. Int J Crit Infrastruct Prot 2(12):5–12. https://doi.org/10.1016/j.ijcip.2009.02.002.
Bompard, E, Wu D, Xue F (2010) The concept of betweenness in the analysis of power grid vulnerability. COMPENG 2010  Complex Eng 52–54. https://doi.org/10.1109/COMPENG.2010.10.
Bompard, E, Pons E, Wu D (2012) Extended topological metrics for the analysis of power grid vulnerability. IEEE Syst J 6(3):481–487. https://doi.org/10.1109/JSYST.2012.2190688.
Bompard, EF, Scala A, Bologna S, D’ G, Casals MR, Pagani GA, Verma T, Ellens W, Agostino NA (2015) Knowing power grids and understanding complexity science. Int J Crit Infrastruct 11(1):4. https://doi.org/10.1504/ijcis.2015.067399.
Chow, JH, Cheung KW (1992) A toolbox for power system dynamics and control engineering education and research. IEEE Trans Power Syst 7(4):1559–1564.
Cuadra, L, SalcedoSanz S, Del Ser J, JiménezFernández S, Geem ZW (2015) A critical review of robustness in power grids using complex networks concepts. Energies 8(9):9211–9265. https://doi.org/10.3390/en8099211.
Delvenne, JC, Yaliraki SN, Barahona M (2010) Stability of graph communities across time scales. Proc Nat Acad Sci 107(29):12755–12760. https://doi.org/10.1073/pnas.0903215107. http://www.pnas.org/content/107/29/12755.full.pdf.
Girvan, M, Newman MEJ (2002) Community structure in social and biological networks. Proc Natl Acad Sci U S A 99(12):7821–7826. https://doi.org/10.1073/pnas.122653799.
Hines, P, Blumsack S, Sanchez EC, Barrows C (2010) The topological and electrical structure of power grids. Proc Annual Hawaii Int Confer Syst Sci 1–10. https://doi.org/10.1109/HICSS.2010.398.
Baldick, R, Chowdhury B, Dobson I, Hawkins D, Kirschen D, Mili L, Miller S, Nakayama M, Papic M, Podmore R, Rossmaier J, Schneider K, Wang D (2009) Vulnerability assessment for cascading failures in electric power systems In: 2009 IEEE/PES Power Systems Conference and Exposition, 1–9.. IEEE. https://doi.org/10.1109/PSCE.2009.4839939.
Kezunovic, M, Xie L, Grijalva S (2013) The role of big data in improving power system operation and protection In: Bulk Power System Dynamics and ControlIX Optimization, Security and Control of the Emerging Power Grid (IREP), 2013 IREP Symposium, 1–9.. IEEE.
Li, W, Tang J, Ma J, Liu Y (2010) Online detection of start time and location for hypocenter in north america power grid. IEEE Trans Smart Grid 1(3):253–260.
Liu, X, Murata T (2009) Community detection in largescale bipartite networks In: 2009 IEEE/WIC/ACM International Joint Conference on Web Intelligence and Intelligent Agent Technology, 50–57.. IEEE. https://doi.org/10.1109/WIIAT.2009.15.
Mei, K, Rovnyak SM, Ong CM (2008) Clusteringbased dynamic event location using widearea phasor measurements. IEEE Trans Power Syst 23(2):673–679.
Messina, AR, Messina AR (2015) Widearea Monitoring of Interconnected Power Systems. The Institution of Engineering and Technology.
Nasiruzzaman, ABM, Pota HR, Mahmud MA (2011) Application of centrality measures of complex network framework in power grid. Proc (Ind Electron Confer) 4660–4665. https://doi.org/10.1109/IECON.2011.6120079.
Newman, MEJ, Girvan M (2004) Finding and evaluating community structure in networks. Phys Rev E 69:026113. https://doi.org/10.1103/PhysRevE.69.026113.
Newman, MEJ (2006) Modularity and community structure in networks. Proc Nat Acad Sci 103(23):8577–8582. https://doi.org/10.1073/pnas.0601602103. https://www.pnas.org/content/103/23/8577.full.pdf.
Pagani, GA, Aiello M (2013) The Power Grid as a complex network: A survey. Phys A: Stat Mech Appl 392(11):2688–2700. https://doi.org/10.1016/j.physa.2013.01.023. http://arxiv.org/abs/arXiv:1105.3338v2.
Pagani, GA, Aiello M (2014) Power grid complex network evolutions for the smart grid. Phys A: Stat Mech Appl 396:248–266. https://doi.org/10.1016/j.physa.2013.11.022.
Pahwa, S, Youssef M, Schumm P, Scoglio C, Schulz N (2013) Optimal intentional islanding to enhance the robustness of power grid networks. Phys A: Stat Mech Appl 392(17):3741–3754. https://doi.org/10.1016/j.physa.2013.03.029.
Rosvall, M, Esquivel AV, Lancichinetti A, West JD, Lambiotte R (2014) Memory in network flows and its effects on spreading dynamics and community detection. Nat Commun 5:4630. Article.
Schaub, MT, Delvenne JC, Rosvall M, Lambiotte R (2017) The many facets of community detection in complex networks. Appl Netw Sci 4(2):4. https://doi.org/10.1007/s4110901700236.
Solé, RV, RosasCasals M, CorominasMurtra B, Valverde S (2008) Robustness of the European power grids under intentional attack. Phys Rev E  Stat, Nonlinear, Soft Matter Phys 77(2):1–7. https://doi.org/10.1103/PhysRevE.77.026102. http://arxiv.org/abs/arXiv:0711.3710v1.
Susuki, Y, Mezic I (2011) Nonlinear koopman modes and coherency identification of coupled swing dynamics. IEEE Trans Power Syst 26(4):1894–1904.
Susuki, Y, Mezić I, Hikihara T (2011) Coherent swing instability of power grids. J Nonlinear Sci 21(3):403–439.
Susuki, Y, Mezic I (2012) Nonlinear koopman modes and a precursor to power system swing instabilities. IEEE Trans Power Syst 27(3):1182–1191.
Xu, Y, Gurfinkel AJ, Rikvold PA (2014) Architecture of the Florida power grid as a complex network. Phys A: Stat Mech Appl 401:130–140. https://doi.org/10.1016/j.physa.2014.01.035.
Yan, J, Zhu Y, He H, Sun Y (2013) Multicontingency cascading analysis of smart grid based on selforganizing map. IEEE Trans Inf Forensics Secur 8(4):646–656. https://doi.org/10.1109/TIFS.2013.2249065.
Zhou, J, Huang N, Sun X, Wang K, Yang H (2015) A new model of network cascading failures with dependent nodes. Proc  Annual Reliab Maintainability Symp 2015May:1–6. https://doi.org/10.1109/RAMS.2015.7105077.
Acknowledgements
Not applicable
Funding
JNK acknowledges support from the Air Force Office of Scientific Research (FA95501710329). This work was also supported by the U.S. Department of Energy (DOE) Office of Science, Office of Advanced Scientific Computing Research (ASCR) as part of the Multifaceted Mathematics for Rare, Extreme Events in Complex Energy and Environment Systems (MACSER) project. A portion of the research described in this paper was conducted under the Laboratory Directed Research and Development Program at Pacific Northwest National Laboratory (PNNL). PNNL is operated by Battelle for the DOE under Contract DEAC0576RL01830.
Availability of data and materials
All data analyzed in this study was generated using the publiclyavailable Power System Toolbox for Matlab, which can be downloaded by request from http://www.eps.ee.kth.se/personal/vanfretti/pst/Power_System_Toolbox_Webpage/PST.html. The parameter definitions for the NPCC140 Bus System are bundled with the toolbox in the file pstdat/data48em.m.
Author information
Authors and Affiliations
Contributions
DD was lead author and conducted the computational analysis under the supervision of PhD advisor JNK. All authors participated in conceiving and designing the study. All authors read and approved the final manuscript.
Corresponding author
Ethics declarations
Competing interests
The authors have no competing interests to declare.
Publisher’s Note
Springer Nature remains neutral with regard to jurisdictional claims in published maps and institutional affiliations.
Rights and permissions
Open Access This article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made.
About this article
Cite this article
Dylewsky, D., Yang, X., Tartakovsky, A. et al. Engineering structural robustness in power grid networks susceptible to community desynchronization. Appl Netw Sci 4, 24 (2019). https://doi.org/10.1007/s4110901901370
Received:
Accepted:
Published:
DOI: https://doi.org/10.1007/s4110901901370
Keywords
 Power system simulation
 Community structure
 Network fault tolerance
 Stability